The system is suitable for use in working applications up to 12 bar / 20 degrees centigrade (6 bar / 90 degrees centrigrade). Pipes are suitable for bending to a radius of 12 x diameter when unsupported or 8 x diameter when supported. Connections and fittings are tested too BS 7291: Class S for thermal cycling test, long term pressure tests, rapid pressure test and pull-out strength.
Polyplumb pipes and fittings are tested to BS 7291@ Parts 1 and 2, which incorporates a pressurised thermal cycling test and a test regime at temperatures of 114 degrees centigrade and 3.5 bar pressure for 1,000 cycles at a duration of 30 minutes per cycle.
The polyplumb system is not suitable for the transportation of gases. Standard Polyplumb pipe is Oxygen permeable and is suitable for all domestic water and heating installations. Polypipe recommends that corrosion inhitors are introduced to, and maintained in, all heating systems, whether they use standard or barrier pipe. Due to the long pipe runs used in floor central heating systems we recommend barrier pipe is used throughtout UFCH applications to minimise the potential for Oxygen ingress into the system.
The polybutylene material used in Polyplumb pipes and fittings is WRC / WRAS approved. It is resitant to the build-up of scale. Short term chlorination for disinfection of supply pipe work and normal levels of chlorine in UK domestic water supplies will not have an adverse effect on Polyplumb. Polyplumb is not suitable, however, for systems that carry a high concentration of chlorine, eg supplies to swimming pools etc.
Polyplumb pipe and fittings should be protected from UV light. Standard decorating paints form adequate protection. Polyplumb pipe insulation forms adequate protection for external use.
The polyplumb system gives better performance than rigid pipe systems in terms of low noise transmission and low water hammer effect.
As Polyplumb pipe does not conduct electricity, installations generally require less equipotential bonding than metal systems. Both the IEE and the IoP give guidance on the eatrth bonding requirements of plastic pipe systems. Where Polyplumb breaks the continuity of existing metal pipe, which may be used for earthing or bonding, this continuity should be reinstated by affixing permanent earth clips and a section of earth cable between the ends of the copper pipe.
Polypipe belive there to be no side-effects from handling or using Polyplumb.
There are six stages to successfully jointing the Polyplumb system. These instructions apply to Polyplumb when used in hot and cold water or heating applications, including floor heating.
Always use one of the approved pipe cutters (PB777 or PB778).
A slight rotation of the pipe when cutting will help make the operation easier. Never use a hacksaw. Wherever possible, cut a depth insertion mark. These "K" shaped marks are equally spaced along the pipe and indicate the depth required for full insertion into a Polyplumb socket fitting.
Pipe stiffeners are an integral part of the joint when using Polyplumb pipe with either Polyplumb fittings or compression fittings, and need to be fully inserted in to the pipe end. They are not required when using copper pipeage.Polypipe
Our delivery charges are calculated based on the weight of your entire order. Below is a table illustrating the cost for each weight bracket, please note we cap our delivery costs to a maximum of £50.
|Weight From (kg)||Weight To (kg)||Cost|
In addition to our standard delivery service, we can also arrange for delivery on a Saturday or before 10.30am on any working day. This level of carriage comes at an additional cost:
We can also arrange for pallet delivery on a three-day delivery, but costs vary depending on the size of the order, so please contact us for details.
Orders placed before 3pm on any business day (Monday – Friday) excluding Bank Holidays should be delivered on the next business day (Excluding Saturday, unless the carriage is met) anytime up to 7.00pm.
Our standard next working day delivery does not guarantee next day delivery; however every effort is made by us and the courier to achieve this goal.
Orders taken on Friday after 3pm, Saturday or Sunday will be dispatched on Monday (excluding Bank Holidays) for delivery on Tuesday up to 7.00pm.
Orders placed on Friday before 3pm will be dispatched on Friday for delivery on Monday up to 7.00pm unless the Saturday delivery charge is met (This excludes Bank Holidays).
Please note: We rely upon the services of third party couriers and, whilst we endeavor to always deliver in a timely manner, there are unfortunately a few occasions when the couriers fail to deliver on the appointed day. This happens rarely, but because it does occur, albeit occasionally, we cannot be held responsible for the late delivery of an item, or any costs incurred by customers tradesman unable to work, please ensure you have your materials before booking in any trades.
Shipments sent outside the European Union may be subject to import duties and taxes, which may be levied once a shipment reaches your country. For details of Customs charges please consult your own Customs authorities for the latest rates.
Additional charges for customs clearance must be borne by you; unfortunately we have no control over these charges and cannot predict what they may be. We are unable to reimburse any costs incurred regardless of the circumstances.